Ремонт пола Устройство теплого полаPro-Remont.com Repair floor machine warm floor
The warm floor
In some rooms : the bedroom, child, the bathroom is not worth the device warm floor.
It can be divided into two types : electric and water. The primary plate fit for the entire area of the premises of a special power cables or pipes connected to the hot water supply, and has made the final top plate.
Electrical floors came to us from Europe, there also supplied and special cables. The heating cable is a key element of the warm floor. In fact, the conductor with a high resistance, which is heated by passing electric current through it. The first time they were dissatisfied environmentalists because of the electromagnetic field created has been, if not great, but still harmful to people. This is now removed : electromagnetic radiation modern cable minimum and has no adverse effects.
To expand the opportunities for optimum savings and comfort used thermoregulators devices with high precision.
But there is a warm electric field and a number of other shortcomings : it consumes electricity from Uzbekistan to 400-ot kilowatt hour. In addition, an exploratory inclusion warm floor only after completely dry seals, or 45 days. If the warm floor is not working, it is necessary to shatter plate, remove the problem and flooded again. By the same lengthy and costly procedures to be used in case of the warm floor in the operation.
Installation Guide heating cable
The performance of heating cable laying for the "warm box"
1. Make a drawing of heated area, which includes heating cable tip and slip sleeve, sensor temperature and connection to the mains. If a heating cable in the presentation or in the process of construction work is easier to find places damaged.
Distance (cm) = free area (sq. m) x 100 / cable length (m)
Temperature sensor is placed between the lines heating cable with an open hand hinges on the distance 50-100 see on the wall.
2. The wall drill shtrobu section 20 x 20 mm sensor to the surface temperature and cold connecting wires and wall thermal boxes.
3. Clear authority, which falls cable from the debris and sharp objects.
4. Lock mounting tape on the floor.
5. Dividing evenly heating cable loop on the surface of the field, passing pipes and sites intended for the bathrooms, lockers, etc. Lock cable for mounting tape through special attachment located every 3 cm.
6. After installing the cable measure resistance resistance. Resistance resistance shall be those specified in the coupling -5% - 10%.
7. Temperature sensor box to put in a plastic tube diameter of 16 mm, dead-end at one end to prevent the entry into the concrete and put heating cables between the lines, according to the charts compiled. Bending the tube diameter must not exceed 6 cm.
8. Evenly pour cable solution that does not contain sharp stones. Heating cables and connective sleeve must be completely sealed off. Plate should not exceed 5 cm.
9. After filling the cable again, observe resistance resistance.
10. Do not include heating cable until solidification solution. Typically, spattered layer solution completely frozen over a period of 30 days. Depending on the solution can be reduced.
11. Connect through thermal heating cable to the electrical grid. No sooner than full day field progreetsya before the temperature.